Product Name: Ayvaz BK-33 TK Thermostatic Steam Trap Valve Station
Product Code: BK-33 TK
Tags: Ayvaz BK-33 TK Trap Valve BK-33 TK Trap Valve Station Ayvaz Thermostatic Steam Trap Ayvaz TK Thermostatic Steam Trap Station Ayvaz BK-33 TK Trap Valve Station BK-33 TK Thermostatic Trap Station Ayvaz BK-33 TK Thermostatic Trap Ayvaz Thermostatic Steam Valve Station Ayvaz Steam Ayvaz BK-33 Steam Trap Ayvaz Thermostatic Valve Station BK-33 TK Steam Valve Thermostatic Steam Trap Valve Station Thermostatic Steam Station Ayvaz Thermostatic Steam Trap Thermostatic Trap Station Ayvaz Steam Trap TK Thermostatic Valve Ayvaz Steam Trap Valve
Thermostatic Steam Trap Valve Station
Are you interested in the product Ayvaz BK-33 TK Thermostatic Steam Trap Valve Station from manufacturer Ayvaz with code BK-33 TK? Contact us now and get offer. Imtek Engineering, the fastest and most reliable industrial equipment supplier in the world, will offer you the best offer!
Get Offer With E-Mail: firstname.lastname@example.org
Get a offer for Ayvaz BK-33 TK Thermostatic Steam Trap Valve Station from our live support team now!
BK-33TK Thermostatic Steam Trap Valve Station contains 2 piston type valves in the flow direction. Optional test valves for steam trap testing and discharging the pipeline are also available.Steam saturation curve is followed with a static difference by the thermostatic element which is highly resistant against corrosion. It is aimed to discharge condensate and non-condensable gases in the steam lines.Resistant against the corrosion and not effected by water hammer.S type capsules are used in standard production.Condensate discharging is constant.BK-33TK can easily be disassembled individually and be maintained.Operating Conditions:Max. Operating Pressure : 21barMax. Operating Temperature: 240 °CMax. Pressure Difference: 21barApplications:Drying UnitsPressesSteam JacketsIronsBK-33 TK, thermostatic steam trap can easily be installed to the pipe connector. Thermostatic steam traps may be installed bot vertically or horizontally to the steam lines. The flow through the pipe connector should be in the arrow direction.