Product Name: Ayvaz BK-33SK Float Type Steam Trap Valve Station
Product Code: BK-33SK
Tags: Ayvaz BK-33SK Type Steam Station BK-33SK Float Type Steam Ayvaz BK-33SK Type Steam Trap Station Ayvaz Float Steam Valve Station Float Type Trap Float Type Steam Trap Station Ayvaz BK-33SK Float Type Trap Valve Station Ayvaz Type Steam Trap Valve Station Type Steam Station BK-33SK Float Type Steam Trap Valve Ayvaz Steam Trap Valve Station Float Station Ayvaz BK-33SK Type Trap BK-33SK Steam Trap Valve Station Ayvaz Float Steam Valve Trap Valve Station Type Trap Valve Ayvaz BK-33SK Float Steam Trap Ayvaz Float Type Steam Trap Ayvaz BK-33SK Type Steam Station
Float Type Steam Trap Valve Station
Are you interested in the product Ayvaz BK-33SK Float Type Steam Trap Valve Station from manufacturer Ayvaz with code BK-33SK? Contact us now and get offer. Imtek Engineering, the fastest and most reliable industrial equipment supplier in the world, will offer you the best offer!
Get Offer With E-Mail: firstname.lastname@example.org
Get a offer for Ayvaz BK-33SK Float Type Steam Trap Valve Station from our live support team now!
BK-33SK Float Type Steam Trap Valve Station contains 2 piston type valves in the flow direction. Optional test valves for steam trap testing and discharging the pipeline are also available.Operates constant discharging at saturation temperature especially where the condensate amount is not fixed.Resistant against the sudden and big pressure changes.BK-33 SK can easily be disassembled individually and be maintained.Beside of the float that operates the liquid discharging, air discharging is controlled by the existing thermostatic capsule.Prevents the water hammerIn case, that the float loses its functionality, thermostatic capsule fulfills the task of condensate discharging.Operating Conditions:Max. Operating Pressure: 32 barMax. Operating Temperature: 286 °CMax. Pressure Difference: 4,5/10/14 barApplications:Drying UnitsPressesSteam JacketsIronsInstallation:BK-33 SK, float type steam trap can easily be installed to the pipe connector. Usually, float type steam traps are installed horizontally to the steam lines. The flow through the pipe connector should be in the arrow direction.